Universal connector (with and without strainer) for use with steam traps. Facilitates quick replacement of traps reducing maintenance costs.
- The universal connector, once installed, remains in the pipeline permanently. The trap itself is attached to the universal connector by two bolts, enabling quick installation and replacement.
- The universal connector design facilitates vertical/ horizontal installation or any angle in-between regardless of piping configuration.
NPS ½, 3/4
Universal connectors are supplied in Screwed (NPT/BSPT/BSP), Socket Weld connections.
The universal connector can be installed in horizontal or vertical lines. The universal connector face must be in a vertical plane. The trap should be fitted to the connector with its cap uppermost. Full-port isolating valves should be installed upstream and downstream of the universal connector.
Remove the cap for periodic cleaning of strainer.
- Once universal connector installed then replacement of steam trap is very easy.
- Maintenance is easy and less time required to replace the trap.
|1||CONNECTOR BODY||ASTM A351 Gr. CF8||01|
|10||STRAINER SCREEN||AISI 304 (Perforated Sheet 0.8)||01|
|11||STRAINER CAP||ASTM A743 Gr. CA40 (Cast Equiv. AISI 420)||01|