Moisture Separator is used to improve the quality of steam or compressed air. As steam or compressed air enters in to the moisture separator, a series of internal baffles separate moisture from the media. Liquid droplets falls below due to gravity which needs to be drained by steam trap or Drain trap
Moisture Saparator can be available with IBR test certificates, on request.
The Moisture Separator should be fitted with the Inlet & Outlet connections horizontally in line according to flow direction arrow marked on body. Drain of moisture separator should be pointed downwards, the steam trap or drain trap is required to be installed at drain point of moisture separator.
½”, ¾”, 1″, 1½”, 2″, 2½”, 3″, 4″, 5″, 6″, 8″, 10″, 12″
Material Of Moisture Separator:
|1||BODY||ASTM A106 Gr B||1|
|2||END PLATE||ASTM A516 Gr.70||2|
|3||INLET/OUTLET FLANGE||ASTM A105||2|
|4||INLET/OUTLET PIPE||ASTM A106 Gr. B||2|
|5||DRAIN FLANGE||ASTM A105||1|
|6||FLANGE PIPE||ASTM A106 Gr. B||1|
|BAFFLE PLATE||ASTM A516 Gr. 70||1|
|½” to 10”||Cast Iron/ Ductile Iron / Carbon Steel/ Stainless Steel|
|DN25 to DN250||Carbon Steel/ Stainless Steel/ Cast Iron/ Ductile Iron|